By Kenton Shepard
This is the exterior of a townhome I was asked to inspect. During the inspection, I ran into a neighbor who told me that the roof of another garage, identical to the one pictured above two buildings down, had collapsed the previous winter under a snow load.
So, I decided to keep my eyes wide open as I went through the garage.
- improper alterations; and
- improper bearing points.
Trusses cannot be altered in any way without the approval of a structural engineer. When you see plywood gussets added at truss connections like these triangular gussets, then an alteration of some sort has obviously been made and you have to recommend evaluation by a structural engineer. So, that condition went into the report
Trusses are designed to bear loads at very specific points. Typical roof trusses should not touch any interior walls and should bear only on the exterior walls. The two trusses at the left of the above photo are bearing on an offset portion of the garage wall.
- inadequate metal connector (hanger);
- inadequate fasteners (deck screws); and
- improper fastener installation (through drywall).
These trusses would have best been supported by bearing directly on wall framing. The next best solution would be an engineer-designed ledger or engineer-specified hardware. And that may have been how they were originally built, but by the time I inspected them, 24-foot roof trusses were supported by joist hangers designed to support 2×4 joists. The hangers were fastened with four gold deck screws each.
Gold deck screws are designed to resist withdrawal. Fasteners for metal connecters such as joist hangers are designed to resist shear.
Withdrawal force is like the force which would be generated if you grabbed the head of a fastener with pliers and tried to pull it straight out.
Shear force is what’s used if you take a pair of heavy-duty wire cutters and cut the fastener. Fasteners designed to resist withdrawal, such as deck screws, are weak in shear resistance.
So, there were drastically undersized metal connectors fastened by badly under-strength fasteners.
To make matters worse, the screws were fastened through drywall, which doesn’t support the shaft of the screw and degrades the connection even further.
Above: gangnail integrity destroyed